Installing Noodoe EV's
AC11P EV CHARGER
HOW TO INSTALL YOUR AC11P CHARGER
|Read this user manual thoroughly and make sure to review all local building and electrical codes before installing the AC charger.
|A qualified technician should install the AC charger according to the user manual and local safety regulations.
|Use appropriate protection when connecting to the main power distribution cable.
|Type B, C or D breaker with a rating current of 60Amp should be installed in the upstream AC distribution box.
|Verify that the Wall Connector is properly grounded.
|Crimpers for ring terminals
|Phillips screwdriver for M4 ~ M6
|1-3/8 inch or 34 mm drill bit
|Voltmeter or digital multimeter (for measuring AC voltage at the installation site)
|The inserting cable should meet the best waterproof performance.
It is recommended to use a 3 core / 6 AWG or 14 mm2 cables (XLPE-75 °C, THHN-75 °C, or equivalent) to pull the cable from the distribution box. The maximum outer diameter of the cable should be 16 mm ~ 23 mm.
|Pencil or marker
|Ring terminal (recommend type 14-5) for 6 AWG wire, and fixed by M5 slotted head screw
|Slotted head screwdriver for M5
Follow the instructions in the User Manual to complete the installation of the EV charging stations.
Noodoe EV charging stations require internet connectivity to complete charger activation and to provide charging services.
If using Wi-Fi, a high-quality commercial-grade 4G router is required for stable operation of the charging stations.
A consumer router will freeze after a few months and require a reset. Commercial-grade routers are designed for years of continuous operation under harsh conditions. Additionally, they can auto-reboot should the routers stop working. This ensures dependable, automated service. Please contact your Noodoe EV representative or distributor if you require help with obtaining a commercial-quality Noodoe-certified 4G router.
After all the electrical work has been completed and the Ethernet cable has been plugged in, you can power up the charging station by turning on the breaker.